Notifier Addressable System
Esser Addressable System
Conventional Fire Alarm Panels
Emergency Voice Comms And PWD System
Firemen Intercom System
Public Address And Voice Alarms
System Sensor Devices
KAC, Kobishi, Solo, Others
Fireray, OSID, Ex-Proof
Home Fire Alarm Device (HFAD)
Hotels & Malls
Industrial Facilities & Infrastructure
Schools & Sport Hubs
(0) Check Enquiry
GS546 Home Smoke Detector
XS100 Home Smoke Detector
Ultra-thin photoelectric smoke alarm device
Big button for hushing
Ten years battery service life
Simple to install
Ambient Light detection function
Certification to EN14604:2005/AC-2008
VDS 3131, CE Certified
Power Source: DC 3V Built-in lithium battery
Quiescent Current: < 10uA
Alarm Sensitivity: 0.1-0.15 dB/m
Alarm Current < 90mA
Alarm Volume: > 85dB(A) @ 3m
Hush Time: 10 minutes± 10%
Battery Service Life: 10 years (approx)
Humidity Range: <95% relative humidity (RH)
Temperature Range: 0°C to 40°C
Size: 115mm diameter x 23.5mm depth
In the operating mode, the red LED will flash once every 40 seconds.
When the smoke detector detects particles of combustion and the concentration of smoke reaches the alarm threshold, the red LED will flash once per second with a pulsating alarm. This alarm will persist until the smoke within the chamber is cleared or when the alarm is manually acknowledged.
It comes with self-testing function that can replace the manual weekly test.(Owners are recommended to test manually at least once a year)
When the battery voltage is below the set threshold, an intermittent chirp will be emitted and the red LED will flash ONCE every 40 seconds.
Sensor Chamber Fault:
If the smoke detection chamber function weakens to below set threshold, a chirp signaling a fault will be emitted. Under this condition, the LED indication will NOT blink.
Buzzer Failure Fault:
In the event of Buzzer failure, the red LED will have TWO flashes every 40 seconds
To silence the detector when it is in an alarm condition, pressing the test button will pause the alarm for approximately 10 minutes. Under this condition, the red LED will flash once every 8 seconds. If the smoke in the chamber is still present, the alarm will resound upon expiry of the silence mode.
Do Not Disturb (Hush):
When the detector is in a fault or low battery mode, pressing the test button will temporarily silence this warning tone for 10 hours. However, the warning signal will resound after 10 hours if the detector is not being attended to. The red LED will flash once every 40 seconds under hush mode.
Home Fire Alarm Device (HFAD) - "Siterwell" GS546
Reliable Home Safety
XS100 Smoke Alarm
Easy to Install & Use
Long life, Discreet Design
Approved by HDB for use in residential flats
Detection Principle – Optical
Clearly visible LEDs : Normal, Fault, Alarm
Loud 85dB audible alarm
Large button - can be pressed with a broom stick
Sealed in battery lasts for 10 years
Low profile design blends into ceiling
On/Off only by installing/removing from mounting plate
Approved to CE EN 14604:2005/AC:2008
Honeywell video edited to show mounting and removal from base.
Refer to user guide for complete information on device workings.
Home Fire Alarm Device Honeywell XS100
XS100 User Guide